For screen reader problems with this website, please call715-343-80007 1 5 3 4 3 8 0 0 0Standard carrier rates apply to texts.
The SNE Series Hybrid is configured for hybrid security systems consisting of a mix of analog and digital equipment and cabling. Accommodates small devices including encoders, power supplies and access control systems on the patented Zero-U Tool-Free Lever Lock™ system. Fully configured Security Network Enclosure w/active ventilation for equipment rooms, 70% open area vented front door, Pair of split flush mount locking side panels, (2) vertical 10” wide Lever Lock™ accessory mounting plate, (1) 6” wide vertical wire grid lace, 24” width, 36” overall depth, 45 rackspace, 2 pair of tapped 10-32 adjustable rail, 4 space cage-nut adapter (pair) SNE Series Hybrid with Top Active Ventilation. Fan top with proportional speed thermostatic control provides 660 CFM ventilation. Solid split door.
EIA compliant 19” gangable digital security network enclosure shall be Middle Atlantic Products model # SNE__D-__-P_ (refer to chart). Fully welded construction shall provide a static capacity of 12,000 lbs., a UL Listed load capacity of 3,000 lbs., and casters shall provide a capacity of 1,600 lbs. SNE shall come equipped with two pairs of fully adjustable steel cage nut rackrail with 6MM mounting hardware in universal EIA spacing, black e-coat finish and numbered rackspaces. SNE shall include 70% vented front door, __rear doors (refer to chart), and flush locking split side panels. SNE shall include pair of Lever Lock™ mounting brackets. SNE shall have pre-threaded 5/16”-18 ganging holes. SNE shall be capable of ganging while fully loaded, using bolts only. SNE shall have passive cooling, front to rear. SNE shall have marked rackrail depth indicators. SNE shall be of fully welded construction. SNE shall be finished in an environmentally friendly, durable black powder coat. SNE Series enclosures shall satisfy the 2007 & 2010 CBC; 2006, 2009 & 2012 IBC; ASCE 7-05 (2005 Edition) & ASCE 7-10 (2010 Edition) and the 2006 & 2009 editions of NFPA 5000 for use in areas of high seismicity, Seismic Use Group III, Zone 4 or Seismic Design Category (SDC) “D” with lateral force requirements for protecting 1,050 lbs. of essential equipment in locations with the highest level of seismicity and top floor or rooftop installations with an Importance factor (Ip) of 1.5 when used with SNE-Z4 seismic floor anchor bracket. SNE shall be UL Listed in the US and Canada to the UL-2416 (NWIN) category. SNE shall be GREENGUARD Gold Certified. SNE enclosure shall be RoHS EU Directive 2002 / 95 / EC compliant. SNE shall be manufactured by an ISO 9001 and ISO 14001 registered company. SNE enclosure shall be warrantied to be free from defects in material or workmanship under normal use and conditions for the lifetime of the rack. Customizable specification clips available at middleatlantic.com
|Finish||Black Powder Coat|
|UL Standards Tested||UL2416|
|Capacity Weight (US)||12000|
|Static Load Capacity||12000|
|UL Load Capacity||3000|
|UL Listing No.||E313734|
|Number of Doors||2|
|Weight Capacity (lbs.)||3000|
|Manufacturer Warranty||Limited Lifetime|