For screen reader problems with this website, please call715-343-80007 1 5 3 4 3 8 0 0 0Standard carrier rates apply to texts.
EIA compliant 19” presentation equipment rack shall be Middle Atlantic Products model #BGR-19SA27MDK-DS. Overall dimensions of BGR shall be 39.5”H x 24.5”W x 27”D. Useable height of BGR shall be 19 rackspaces, useable depth shall be 24-2/5”. BGR shall come equipped with two pairs of fully adjustable steel rackrail with two 10-32 threaded holes per side of each marked rackspace, and a cage-nut style mount that is compatible with tool-free Forward Series rackmount accessories. BGR rackrail shall include cable management lacing provisions and accept tool-free Forward Series cable management accessories. BGR shall have .100”thick steel along rackrail brackets, .310” thick steel at corners. BGR shall include vented locking and latching rear door, which shall be capable of accepting up to six 4-1/2” fans. Top and bottom of BGR shall feature vertical slotted vent pattern for ventilation. BGR shall have two 1” x 7”rear obround knockouts with 1/2”, 1”, 1-1/4” and 1-1/2” electrical knockouts and 5/8” and 1/2” D UHF/ VHF antennae knockouts in base and top. BGR shall have a configurable open top with vertical cable management entry points. BGR shall accept patent-pending LeverLock™ tool free and hardware free internal cable and device management system accessories. BGR shall have pre-threaded 5/16”-18 ganging holes. BGR shall be capable of ganging while fully loaded, using bolts only. BGR shall have marked rackrail depth indicators. BGR shall be of fully welded construction. BGR shall be finished in an environmentally friendly, durable black powdercoat. Grounding and bonding studs shall be 1/4-20 threaded, installed in top and base of enclosure (19 and 25 space have stud in bottom only). Fully welded construction shall provide a UL Listed load capacity of 3,000 lbs. BGR Series enclosures shall satisfy the 1997 UBC; 2001, 2007 & 2010 CBC; 2000, 2003, 2006 & 2009 IBC; ASCE 7-02, ASCE 7-05, ASCE 7-10 and the 2003, 2006 & 2009 editions of NFPA 5000 for use in areas of high seismicity, Seismic Use Group III, Zone 4 or Seismic Design Category (SDC) “D” with lateral force requirements for protecting 1,175 lbs. of essential equipment in locations with the highest level of seismicity and top floor or rooftop installations with an Importance factor (Ip) of 1.5 when used with BGR-Z4 or BGR-ISO-Z4 (isolated) seismic floor anchor bracket. BGR shall be OSHPD approved for fixed equipment anchorage in California healthcare facilities. BGR shall be UL Listed in the US and Canada. BGR shall be GREENGUARD Gold Certified. BGR enclosure shall meet the RoHS EU Directive 2011/65/EU. BGR shall be manufactured by an ISO 9001 and ISO 14001 registered company. BGR enclosure shall be warrantied to be free from defects in material or workmanship under normal use and conditions for the lifetime of the rack.
|UL Standards Tested||UL1678|
|UL Load Capacity||1100|
|UL Listing No.||E173107|
|Number of Doors||2|
|Weight Capacity (lbs.)||1100|
|Manufacturer Warranty||Limited Lifetime|